Payment & Shipping Terms:
|Keywords:||Zinc Oxide Surge Arrester||Material:||Silicon Rubber|
|Housing:||Polymer, Composite, Silicone Housing||Rated Voltage:||36KV|
|Nominal Current:||10KA||Accessory:||Bracket,Insulating Cap,Cooper Lead,Insulator,Hoop|
gapless lightning arrester,
Polymeric Surge Arrester
5KA Kema Tested Polymer Metal Oxide Composite Surge Arrester with Insulating Bracket
0.28kV~500kV Surge Arresters' Characteristics:
1. The Core column applied winding structure, Polymer Housed core pillar molded on the core column, with almost no internal air gap, and outstanding sealing performance Simple in structure, small in size and light in weight.
2. Polymer Housed with silicone rubber, explosion-proof ZnO varistor as the core component is large
in flow capacity.
3. International standard IEC 60099-4 and ANSI 62.22, and with high reliability. With fully insulated tops, the product can be applied to the complete cabinet installation, which can reduce the designing size of cabinet.
4. Products with detachment device can provide signals for quitting operation when failure occurs,
avoiding arrester explosion, and it is maintenance-free.
5. Polymer housed products with a six CTI level, creepage distance meets the requirements of IV level in heavy pollution areas.
1. Compact and Lightweight
2. Extremely Safe Pressure Relief Performance
3. Superior Performance against Environmental Contamination
4. Directly Molded Structure
5. Compliance with International Standards(IEC60099-4)
6. Simple Support Structure
7. Manufactured at Advanced ISO-9001 certified facilities
1. Distribution networks
2. Transmission line
4. Railway power station
5. Alternator and electromotor
Composite Surge Arrester Specifications:
|Residual voltage of steep impulse----at 5kA(kV)||106|
|8/20µS Residual voltage of lightning impulse current kV(Peak value)-----at 5kA(kV)||98|
|Residual voltage of switching impulse current kV (peak value)----at 1kA (kV)||75|
|1mA D.C reference voltage (kV)||51|
|Line discharge level||1|
|2mS long duration impulse current A||400|
|4/10µS High current impulse kA||100|
|Lightning impulse withstand kV||200|
|Power frequency voltage withstand(dry/wet)kV||70|
|Creepage distance ----mm||1148|
|Material employed in series non-linear resistor||Zinc Oxide|
1 Applicable stardand:IEC,ANSI,GB and other international standard
2 Normal colour of the surge arrester: red, gray and brown.
3 Special design according customer’s requirement.
Contact Person: Matt